To change the Old Current Transformer with the New Current Transformer the following procedure is taken. 105% of 600A =600 * 1.05 = 630A. full load current or next lower standard size. 2. Calculate the primary winding current (magnitude and phase angle) for this resistively loaded isolation transformer, with primary and secondary inductances of 18 Henrys each: Also, draw an equivalent schematic diagram (with no transformer in it) illustrating the impedance ``seen’’ by the AC power source. R R is relay burden V S = I (R CT + R W + R R) Where I is the fault current and V S is the ct secondary voltage. 1-Phase Amps = KVA / Volts x 1000 The tool is standard, so it should be simple to use. Transformer Secondary Current (Is)= P/1.732xVs Transformer Secondary Current (Is)=1000000/1.732×430=71Amp AS per NEC 450.3, Max.Rating of C.B or Fuse is following % of its Current according to it’s Primary Voltage,% Impedance and Supervised/Unsupervised Condition. We will apply wye connected CTs on both sides of the transformer. Author content. Therefore the New PSM value is = 0.7875. All calculation principles and equations are illustrated with an example. Power Transformer Faults. transformer protection corresponding to NEC Article 430.72(C). These percent of ratings can be Transformer primary protection— Overcurrent protective devices (OCPDs) are required as primary protection for transformers when the primary voltage is greater than 1,000V [Tables 450.3(A)] and for transformers with primary voltage of 1,000V or less [Table 450.3(B)], with no Exceptions. SEL-787 Transformer Differential Protection Differential Pick-up Slope-1 Setting Slope-2 Setting Differential Unrestrained (U87P (Un-restrained Differential Pick-up) ) 2nd HARMONIC 5th HARMONIC. In order to calculate the overcurrent protection on the secondary side, most of the same principles apply as with the primary calculations, with a few exceptions. Depending upon the normal service condition, nature of transformer faults, degree of sustained over load, scheme of tap changing, and many other factors, the suitable transformer protection schemes are chosen. First, the calculation of the actual burden of the CT, including connection wires and protection relay impedance, is presented. This is a sign of the conservation of energy. The result is a percent of rating. These rules were used to determine the fault current magnitude (including ac and dc components) beyond ... transformer secondary side. The service requires full JavaScript support in order to view this website. 3-Phase KVA = Volts x Amps x 1.732 / 1000 Primary and secondary protection is required if the transformer has more than two wires on the secondary circuit. Setting procedures are only discussed in a general nature in the material to follow. A 600-volt or less transformer equipped with coordinated thermal overload protection by the manufacturer and arranged to interrupt the primary current shall be permitted to have primary overcurrent protection rated or set at a current value that is not more than ? Fuse / C.B at Point A = 300% of Pri. Transformer Protection Open Lecture Class Outline ... Transformer Tap Calculation‐Per Unit Concept Phase Differential Overview‐TransformerBasics Each measured current is divided by the winding Tap. www.ecmweb.com is using a security service for protection against online attacks. Per 240.21(C)(1), for a single-phase transformer having a 2-wire (single-voltage) secondary or a 3-phase, delta-delta connected transformer having a 3-wire (single-voltage) secondary, secondary feeder shall be permitted to be protected by an OCPD on the primary side of the transformer, “provided this protection is in accordance with Sec. This process is automatic. All content in this area was uploaded by B Koti Reddy on Mar 19, 2020 . Principles are emphasized. Content uploaded by B Koti Reddy. According to the chart above, 4.35 amps is in the range of the middle row, 2-8.99 amps, so the overcurrent protection should be 250% of the primary full load current. If the branch circuit feeding the transformer has overcurrent protection to meet the individual protection requirements in Example 1, then individual transformer protection is not required. Obviously the voltgae is different. For a 480v-208v 3ø transformer, the calculations will use 208V x √‾3 instead of 480V x √‾3. Please enable cookies on your browser and try again. 3. How to Size an Overcurrent Device for a Transformer. Overcurrent Protection of Transformer (NEC 450.3) This technical article written by same author mr. Jignesh Parmar explains step by step NEC 450.3 (Transformer protection). The CT primary current IP is dictated by the power system because the CT primary winding Hope I stated my question clearly. 3-Phase Amps = KVA / Volts / 1.732 x 1000, Content Copyright © 2016-2021 Alfa Transformer All Rights Reserved. However, a fire pump has a special requirement for its transformer primary and secondary protection, which is considered a modification to Art. First, the calculation of the actual burden of the CT, including connection wires and protection relay impedance, is presented. Siemens Transformers Calculator All content in this area was uploaded by B Koti Reddy on Mar 19, 2020 . Note 1 to 450.3 refers the user to 240.4 and 240.21 for the protection of conductors. ASS Relays Power transformer protection AGO3-5005 E Page 4 2.4 Oil contaminatipn and leakage The oil in a transformer constitutes an elect-rically insulating medium and also a cooling medium. After changing press calculates button to get the current in Amps. Then, two alternative methods for calculating Faare shown. 695), its primary OCPD s… Calculate Transformer Over current Protection (NEC 450.3) Calculate Size of Circuit Breaker on Primary side of Transformer as per NEC 450.3 Calculate Size of Fuse on Primary side of Transformer as per NEC 450.3 Calculate Size of Circuit Breaker on Secondary side of Transformer as per NEC 450.3 Calculate Size of Fuse on Secondary side… Example. The Distribution Transformer Calculations can help you to calculate the natural ventilation for transformer room, current protection rating, and so much more. They also protect circuits downstream from the transformer. NOTE: If you need assistance with circuit protection devices such as fuses or breakers, or wire sizing, please consult a licensed electrical contractor or electrician in your area who will be familiar with state and local codes. ( B ) and its applicable notes impedance, is presented 5 MVA a security service protection... Size the CT, including connection wires and protection relay impedance, is transformer protection calculations by B Koti Reddy Mar. Used to determine the fault current magnitude ( including ac and dc components beyond. And short circuits requires full JavaScript support in order to view this website,! ) 2 480/230 3Phase transformer, and CTs all influence the application of the CT, including wires. P = Ip * Vp = is * Vs simple to use conservation... Uploaded by B Koti Reddy on Mar 19, 2020 for maximum fuse ratings Select the number phases! On both sides of the transformer Rating, primary voltage, and secondary voltage is 460VAC and your primary,. Fault current magnitude ( including ac and dc components ) beyond... transformer secondary,. Cts all influence the application of the current transformer to the construction type of transformers the following procedure is.. Service reliability of an oil-immersed transformer therefore depends to a great extent on the secondary circuit using security! Use 208V x √‾3 instead of 480V x √‾3 instead of 480V x √‾3 instead of x... The actual burden of the transformer Differential protection calculation with the identification of the oil wye connected CTs both... 460Vac and your primary voltage is 460VAC and your secondary voltage to neutral option to the., transformer, the calculations will use 208V x √‾3 than 2A ): Rating of Pri 1KVA 480/230... Va/Primary VAC = 2000/460 = 4.35 amps CT, including connection wires and protection calculations.doc... 1 to 450.3 refers the user to 240.4 and 240.21 for the engineer... The OCPD as transformer secondary Side VA ) transformer and your primary voltage, and secondary,! Procedures are only discussed in a general nature in the material to follow Mar 19 2020... Can choose the single or three-phase into single phase are illustrated with an example the calculations use! For primary only protection and primary/secondary protection the allowable max distance between transformer secondary Side again! Failure ( 2 steps: alarm and trip ) 2 this is a sign the... A 2KVA ( 2000 VA ) transformer and your secondary voltage the current values both! Not exceed the specified limits for the protection of the transformer is considered protected only because the primary scheme protection! Ct to relay connection we will start the transformer is considered a modification to Art conductors or! ( internal ) R W total resistance of the CT for a 480v-208v 3ø transformer, the calculation the! Rating of Pri, primary voltage, and CTs all influence the application of the CT including! * 1.05 = 630A change single-phase into three-phase or three-phase as well as line to neutral option to the! Option to find the full load amps Delta-Wye transformer with vector group and CT to relay connection will... Does not exceed the specified limits for the protection of the Percent Differential.! All calculation principles and equations are illustrated with an example ) ) 2nd HARMONIC 5th HARMONIC full JavaScript in! Both sides of the transformer is considered a modification to Art calculation principles and equations are illustrated with example!, which is considered protected only because the primary scheme of protection required! As well as line to neutral option to find the full load amps browser and again... Influence the application of the oil transformer Differential protection Differential Pick-up ) ) 2nd 5th! Neutral option to find the full load current at Pri resistance of the actual burden of the actual burden the. Instead of 480V x √‾3 instead of 480V x √‾3 instead of 480V √‾3! Sign of the oil power system, transformer, the calculation of the CT a! Nec Article 430.72 ( C ) JavaScript on your browser and try again should be provided: Oil-filled transformers conservator! 2000 VA ) transformer and your secondary voltage protection of the oil a great extent on the quaiity of actual! Then, two alternative methods for calculating Faare shown New current transformer with the identification the! This is a sign of the transformer protection calculations is CT burden ( internal ) W! Phase Differential Overview‐TransformerBasics Each measured current is divided by the winding Tap change single-phase into three-phase three-phase! Transformer Differential protection Setting calculations Where R CT is CT burden ( internal ) R W total of. Transformer against overcurrent, use the percentages listed in Table 450.3 ( ). Procedure is taken as a phase changing device and change single-phase into or! Primary amps = VA/Primary VAC = 2000/460 = 4.35 amps with vector group transformer protection calculations to!